Basic Electrical Codes
This article describes some of the more common electric codes questions.
Most electric codes for outlets are found in the International Residential Code, IRC section 3901, 3902 and 4002 and the 08 National Electric Code, NEC section 210
Most lighting electric codes are found in the 2009 IRC 3903, 4001, 4003 and 4004 and 08 NEC sections
Most appliance electric codes are found in 2009 IRC T4101, 3702 and 3905 and the 08 NEC 314, 422, 424 and 440
GFCI Required Locations
- GFCI stands for ground-fault circuit interrupter. Both electric codes require GFCI circuits in bathrooms, garages, crawl spaces, unfinished basements, kitchens, wet bars with sinks, outdoors, outbuildings.
GFCI Outlets In The Kitchen
- Countertop Outlets: To protect people working in the kitchen with appliances around water section 210.52(B) of the National Electric Code requires all countertop outlets to be ground-fault circuit interrupter (GFCI) protected.
- Sink Receptacle: A receptacle must be within 2 feet of the end of the sink.
- Receptacle Countertop Seperation: The maximum distance between receptacles over the counter tops is 4 feet, this is measured along the wall not the front of the counter.
- Circuits Required In Kitchen: The kitchen, dining room and pantry are required to have a minimum of 2 20-ampere circuits. see our article on Wiring a GFCI Outlet for more information.
- Dedicated Circuits: The two kitchen GFCI circuits are each dedicated, meaning that they cannot supply power to anything else except the kitchen outlets.
- Kitchen Island: If you have an island it needs to have a outlet on it. If it is large it will need a GFCI at each end but electric codes only require one. [09 IRC
- Countertop Outlet Height: Counter top receptacles can be no more than 20 inches above the counter top [09 IRC
GFCI Outlets In The Bathroom
- Bathrooms and Outlets: Bathrooms must have GFCI protection.
- GFCI In Bathroom Connected to Other Areas: circuit can be on the same circuit as another bathroom, garage, or exterior GFCI outlet.
- Sink Receptacle: A receptacle is required within 3' of the sink [09 IRC
- Receptacles and Showers or Tubs: No receptacles are allowed directly over or inside the shower or tub space [09 IRC
Wiring Support and Protection
- Nail plates are required if there is less than 1 1/4 of wood between the cable and the face of the framing.
- Cables must be supported within 8 inches of a plastic electric box (with a cable staple) NEC article 314.17(C)
- Cables must be supported at least every 4'-6" by a framing member or other support.
- The refrigerator must be on a circuit other than the GFCI circuits.
- It is wise to put it on its own dedicated 15 amp circuit so that it can't be tripped by something else and spoil the food.
Hallways and Habitable Rooms
- Any wall that is longer than 2' in a bedroom needs to have a receptacle. [09 IRC
- No point on a wall should be farther from a receptacle than 6 feet horizontal (the idea is that the receptacle serves an area 6 feet on each side of the receptacle). This generally means that there shoud be a receptacle every 12 feet or less. The horizontal measurement is along the wall surface, you can't cut corners.
- There should be a receptacle within 6 feet of a door.
- Switched receptacles must be half hot to be included in the "within 6 foot of a receptacle" rule.
- Hallways that are longer than 10 feet must have a receptacle.
- Any unfinished room or area of the basement must have a GFCI protected receptacle.
Smoke Detector Code
- Smoke alarms are required in sleeping rooms and adjacent areas.
- Smoke alarms need to be wired in series so the activation of one sets the others off.
- Smoke alarms must have electric power from the building and a battery back up if the power goes off.
Basements and Garages
- Basements and garages must have one general outlet in addition to outlets installed for a specific use for something like a clothes washer or freezer. [09 IRC
- Every part of a basement that is unfinished must have a receptacle [09 IRC
Copyright © 2010 icreatables. All rights reserved.